Verified by manufacturer 11 months ago
SUPALUX® - Fire Protection To Service Enclosures - 2440 x 1220 mm
Fire protection to general building services.
Provide fire protection to service enclosures.
For the provision fire resisting constructions to general building service enclosures, 120 or 240 minutes fire resistance (integrity only) in accordance with performance criteria of BS 476-20.
Promat constructions have been tested in accordance with the criteria of BS 476-20 and assessed to the criteria of BS 476-24. These assessments include allowance for both internal and external fire.
Features and benefits:
A non-combustible calcium silicate board reinforced with selected fibres and fillers. It is formulated without inorganic fibres and does not contain formaldehyde.
Etex Building Performance Limited warrants that our passive fire protection products and component parts, when installed in the building originally designed, built and unaltered in accordance with the conditions and procedures set out in Promat Passive Fire Protection Handbook, this specification document and associated CAD drawings; and any specific technical recommendations made in relation to the above project, shall be durable and free from defects due to faulty manufacturing or factory workmanship.
The system must be installed by a 3rd party accredited fire protection contractor, and where included in the specification, solely with proprietary products and components as supplied by Etex Building Performance Limited.
The scope of this warranty will be dependent on the application and the environment in which the products are being installed.
2440 x 1220 mm
2500 x 1250 mm
To BS EN:13501-1, Class A1.
Non-combustible with a reaction to fire Classification of A1 according to BS EN:13501-1
Assessment WF No 168498.
Promat SUPALUX® fillet (various dimensions dependent on service enclosure selected).
Promat SUPALUX® (various thicknesses dependent on service enclosure selected).
M4 self tapping screws.
M4 screws into non combustible plugs.
PROMASEAL® Intumescent Sealant.
Promat SUPALUX® service enclosure can be installed horizontal or vertical.
120 to 240 minutes integrity.
For Promat SUPALUX® service enclosure, fire protection provided is SE120 to SE240 minutes stability and Insulation.
Solid or structural wall/floor that provides at least the same fire performance as required from the Promat SUPALUX® system.
Up to 80%.
Boards can be installed before the building is watertight and are suitable for areas where the humidity is up to 85%.
2440 x 1220 mm.