Modified epoxy intumescent coating.
Commercial, industrial, public and transport buildings such as:
All steel surfaces to be coated should be clean, dry and free from contamination prior to application. Consult manufacturer for more details on surface preparation.
Two-component, modified epoxy intumescent coating for cellulosic passive fire protection (PFP). Low volatile organic compound (VOC) and boron-free coating designed to provide fire protection to structural steelwork.
Features and benefits
Light Grey (Part A - Black; Part B - White).
Two-component, modified epoxy intumescent coating.
M61/110 On-site coating to primed steel
M61/115 On-site coating to galvanized steel
M61/120 On-site coating to existing steel
M61/140 On-site overcoating to existing steel
M61/150 Off-site coating to unprimed steel
M61/160 Off-site coating to primed steel
M61/170 Off-site coating to galvanized steel
To ISO 3233.
1 kg provides 1 mm of fire protection.
At 10°C hard dry. Touch dry, 16-hours.
(At 15°C: Touch dry, 16-hours. Hard dry, 22-hours. At 25°C: Touch dry, 7-hours. Hard dry, 16-hours. At 40°C: Touch dry, 3-hours. Hard dry, 4-hours.)
To EPA Method 24.